On December 3, 2010, the SCAQMD adopted Rule 1415.1
(PDF, 154kb) to control emissions of high-global warming potential (GWP) refrigerants used in stationary, non-residential refrigeration systems
. With the adoption of Rule 1415.1, refrigeration systems with a full charge capacity of greater than 50 pounds of high-GWP refrigerants are now regulated solely under the new rule. Such systems are typically used in supermarkets, cold storage warehouses, food processing plants, and process cooling operations. Rule 1415.1 is equivalent in every aspect to the Refrigerant Management Program (RMP)
, a statewide regulation adopted by the California Air Resources Board (CARB) to reduce emissions of high-GWP gases from stationary refrigeration systems. The RMP took effect January 1, 2011.
Rule 1415.1 requires an owner or operator of a stationary, non-residential refrigeration system to submit a plan to the SCAQMD annually. As of March 1, 2016, all applicable refrigeration systems are required to register with CARB
through the RMP.
Registration and reporting to CARB is required according to the following schedule:
|Large Facilities (≥2,000 pounds) |
January 1, 2011
|Medium Facilities (≥200 but <2,000 pounds) || |
March 1, 2014
|Small Facilities (>50 but <200 pounds) || |
March 1, 2016
In addition, the owner or operator is required to:
- Conduct leak inspections, i.e., monthly, quarterly, or annually based on the refrigeration system's full charge capacity, unless automatic leak detection devices are installed;
- Repair any refrigerant leak within 14 days of initial leak detection;
- Keep on site records of all leak inspections, leak repair work and other servicing of the refrigeration system, including receipts of refrigerant purchases; and
- Submit an Annual Report to CARB, when required.
Rule 1415.1 also contains requirements for any person who installs, repairs, maintains, services, relocates, or disposes of any refrigeration system, and for any person who recycles, recovers, reclaims, distributes or sells high GWP refrigerants.